|Published (Last):||20 August 2013|
|PDF File Size:||1.26 Mb|
|ePub File Size:||7.49 Mb|
|Price:||Free* [*Free Regsitration Required]|
Honeywell Vision Pro Manual – Download Manual PDF Online
Heat and cool settings must be at least 2 degrees apart. Remote Sensor Setup Function If an optional remote indoor sensor is installed, the thermostat will display the temperature at the sensor location the internal sensor in the thermostat is not used.
Failure to follow these instructions can damage the product or cause a hazardous condition.
When the outdoor temperature is below the lockout temperature, only the auxiliary heat operates. Plug wall opening with non-flammable insulation.
Honeywell VisionPRO TH8000 Manual
If an optional outdoor sensor is installed, the thermostat can display the outside temperature. When the outdoor temperature is above the auxiliary lockout temperature, only the compressor operates. Download free user manual service manual owners manual operating instructions repair in PDF format.
When set to Auto, the thermostat automatically selects heating or cooling depending on the indoor temperature. Push excess wire back into the wall opening. If function is set to On, the heat and cool settings must be at least 5 degrees apart.
To prevent equipment damage, avoid cycling the compressor quickly. Auto Changeover Setup Honeydell When the outdoor temperature is below the compressor lockout temperature, only the auxiliary heat operates. Contact your local waste management authority for instructions regarding recycling and proper disposal.
When the outdoor temperature is honeywell pro 8000 manual pdf download the lockout temperature, only the compressor operates. Heat Pump Temperature Lockout with fossil-fuel backup: Remove factory-installed jumper only for two-transformer systems. TH models monitor the indoor humidity level and automatically activate the cooling system to reduce humidity by lowering the temperature by up to 3 degrees below the current cool setting.
If this product is replacing a control that contains mercury in a sealed tube, do not place the old control in the trash. Compressor protection is bypassed during testing.
Align pins on back of thermostat with slots in wallplate, then push gently until thermostat snaps into place. Dehumidification control Setup Function If the thermostat is installed with an optional outdoor sensor, you honeywell pro 8000 manual pdf download select a compressor lockout temperature Function If the outdoor temperature is between the compressor and auxiliary lockout temperatures, both the compressor and auxiliary heat can operate. Compressor Protection Setup Function Heat Pump Temperature Lockouts with electric heat backup: Forces the compressor to wait a few minutes before restarting, to prevent damage.
Adaptive Intelligent Recovery Setup Function